Mitsubishi GOT1000 GT15-C08CF Card User's Manual PDF
Summary of Content for Mitsubishi GOT1000 GT15-C08CF Card User's Manual PDF
GT15-CFEX-C08SET Set of GT15-CFEX, GT15-CFEXIF, and GT15-C08CF
Thank you for choosing Mitsubishi Electric Graphic Operation Terminal (GOT).
2006 MITSUBISHI ELECTRIC CORPORATION
GT15 CF card extension unit
Prior to use, please read both this manual and detailed manual thoroughly to fully understand the product.
SAFETY PRECAUTIONS (Be sure to read these instructions before use.)
Before using this product, read this and relevant manuals carefully and handle the product correctly with full attention to safety. Note that these precautions apply only to this product. In this manual, SAFETY PRECAUTIONS are classified into 2 levels: "WARNING" and "CAUTION".
Under some circumstances, failure to observe the CAUTION level instructions may also lead to serious accidents. Be sure to observe the instructions of both levels to ensure the safety. Please keep this manual in a safe place for future reference and also pass this manual on to the end user.
Indicates that incorrect handling may cause hazardous conditions, resulting in death or severe injury.
Indicates that incorrect handling may cause hazardous conditions, resulting in medium or slight personal injury or physical damage.
Do not bunch the control wires or communication cables with the main circuit or power wires, or lay them close to each other. As a guide, separate the lines by a distance of at least 100mm (3.94 inches) otherwise malfunctions may occur due to noise.
Be sure to shut off all phases of the external power supply used by the system before mounting or removing this unit to/from the GOT. Not doing so can cause the unit to fail or malfunction.
When installing this unit, wear a wrist strap to prevent the unit from being damaged by static electricity.
Be sure to shut off all phases of the external power supply of the GOT main unit before connecting the cable to this unit. Not doing so can cause the unit to fail or malfunction.
[Startup and maintenance precautions]
Use this unit in the environment that satisfies the general specifications described in the User's Manual for the GOT used. Not doing so can cause an electric shock, fire, malfunction or product damage or deterioration.
When installing the GOT side installation unit, fit it to the connection interface of the GOT and tighten the mounting screws. When installing the control panel side installation unit, install it on the control panel and tighten the screws of the installation fittings. If the screw is too loose, it may cause a drop of the unit, a failure or malfunctions. Tightening the screw excessively may damage the screw and/or the unit, resulting in a drop of the unit, a failure or malfunctions.
When installing a CF card into this unit, be sure to insert it into the card slot of this unit.
Before inserting or removing a CF card into/from this unit, turn the CF card access switch off. Failure to do so may corrupt data on the CF card.
When removing a CF card from the GOT, support it by hand, as it may pop out. Failure to do so may cause the CF card to drop from the unit, resulting in a damage or failure.
Be sure to shut off all phases of the external power supply used by the system before wiring. Failure to do so may result in an electric shock, product damage or malfunctions.
Carefully prevent foreign matter such as dust or wire chips from entering this unit. Failure to do so may cause a fire, failure or malfunctions.
Plug the cable into the connector of the connected unit and tighten the mounting screws. If the screw is too loose, it may cause a short circuit or malfunctions. If too tight, it may damage the screw and/or the unit, resulting in a short circuit or malfunctions.
Be sure to shut off all phases of the external power supply of the GOT main unit before starting cleaning. Not doing so can cause the unit to fail or malfunction.
Do not disassemble or modify this unit and CF card. Doing so can cause failure, malfunctions, personal injuries and/or a fire.
Do not touch the conductive and electronic parts of this unit directly. Doing so can cause a unit malfunction or failure.
The cable connected to this unit must be run in a duct or clamped. Not doing so can cause the unit or cable to be damaged due to the dangling, motion or accidental pulling of the cable or can cause a malfunction due to a cable connection fault.
When unplugging the cable connected to this unit, do not hold and pull the cable portion. Doing so can cause the unit or cable to be damaged or can cause a malfunction due to a cable connection fault.
Do not drop or apply strong impact to this unit or the CF card. Doing so may damage the unit or CF card.
Before handling this unit, touch a grounded metal object to discharge the static electricity from the human body. Failure to do so may cause failure or malfunctions of the unit.
When disposing of the product, treat it as an industrial waste.
MANUAL The following shows manuals relevant to this product.
For relevant manuals, refer to the PDF manuals stored in the DVD- ROM for the drawing software used.
Compliance with the EMC and Low Voltage Directives To configure a system meeting the requirements of the EMC and Low Voltage Directives when incorporating the Mitsubishi GOT (EMC and Low Voltage Directives compliant) into other machinery or equipment, refer to "EMC AND LOW VOLTAGE DIRECTIVES" of the General Description included with the GOT used. The CE mark, indicating compliance with the EMC and Low Voltage Directives, is printed on the rating plate of the GOT.
Compliance with the new China RoHS directive GOT
SJ/T11364 : GB/T26572
Referenced Standard: GB/T15969.2 (Requirement of Chinese standardized law)
Make sure to transport this unit in the manner it will not be exposed to the impact exceeding the impact resistance described in the general specifications of the User's Manual for the GOT used, as it is a precision device. Failure to do so may cause the unit to fail. Check if the unit operates correctly after transportation.
Manual name Manual number
GT16 User's Manual (Hardware) (Sold separately)
GT15 User's Manual (Sold separately)
Note: This symbol mark is for China only.
This User's Manual describes the GT15 CF card extension unit (hereinafter referred to as the CF card extension unit). For GOT to which the units can be installed and usable CF cards, refer to the User's Manual for the GOT used.
When using an additional drive, the CF card extension unit can be used as the B drive of the GOT. The extension units used as the B drive of the GOT are a CF card unit and a CF card extension unit. The CF card unit and the CF card extension unit cannot be used at once.
When using the CF card extension unit, the control panel side installation unit on the control panel has the CF card interface. Therefore, when inserting or ejecting the CF card, there is no need to open the control panel's door.
When using the CF card extension unit, set the Communication Settings. For setting, refer to the User's Manual for the GOT used.
The following table shows the performance specifications of the CF card extension unit. The general specifications of the CF card extension unit are the same as those of the GOT. For the general specifications of the GOT, refer to the User's Manual for the GOT used.
* When changing the dustproof rubber to the CF card cover fixing screw, the specification for the protective structure is IP67.
Model Product Quantity
GT15- CFEX- C08SET
Control panel side installation unit 1
Installation fitting 2
CF card cover fixing screw 1
GOT side installation unit 1
Fixing screw for GOT side installation unit 2
Shorting bar 1
GT15-C08CF Connection cable (0.8m) 1
- GT15 CF card extension unit User's Manual (This manual) 1
Internal current consumption (5VDC) 0.15A (Total current of GT15 -CFEX and GT15-CFEXIF)
Outside the enclosure
CF card cover closed IP67 or IP65 *
CF card cover opened IP2X
Inside the enclosure IP2X
Weight 0.47kg (1.03lb)
CF card extension unit
3. PART NAMES AND EXTERNAL DIMENSIONS
(1) GOT side installation unit
Dimensions of X when installing the unit on the GOT
Unit: mm(inch) (2) Control panel side installation unit
GOT GT16 GT15
15" 18.5 (0.73) 20 (0.79)
12.1" 17 (0.67) 17 (0.67)
10.4" 20 (0.79) 20 (0.79)
8.4" 22 (0.87) 22 (0.87)
5.7" 22 (0.87) 22 (0.87)
No. Name Description
1) CF card access LED LED lamp lit when the CF card is accessed
2) CF card access switch
Switch for disabling the access to the CF card ON: Access to the CF card enabled OFF: Access to the CF card disabled
3) Eject button Button for removing the CF card
4) CF card cover Cover opening/closing at CF card installation/removal
5) Cable connector Cable connector for connecting the GOT side installation unit and the control panel side installation unit
6) CF card connector Connector for installing the CF card
7) Rating plate -
8) Fixing screw for GOT side installation unit
Fixing screw fixed with a front extension unit or the GOT
9) Hole for unit installation fitting
Hole for the fitting installing the unit to the control panel
10) Dustproof rubber Rubber for blocking the CF card cover fixing screw hole
X Unit: mm (inch)
10) 6) 2)1) 3)
Unit: mm (inch)
4. INSTALLATION PROCEDURE
The installation procedure for the CF card extension unit is explained using the GT1575.
4.2 Installing on the control panel
(2) Fix the GOT side installation unit by tightening its fixing screws (2 places) with a tightening torque of 0.36 to 0.48Nm.
(3) Insert the connector with the ground cable into the GOT side installation unit, and insert the connector without the ground cable into the control panel side installation unit. (For GT1655 and GT155 , before connecting the connection cable to the GOT side installation unit, connect the ground cable of the connection cable to the GOT's terminal block. Because the GOT's terminal block overlaps with the connection cable, the ground cable cannot be connected to the GOT's terminal block.) After inserting the connectors, tighten the connection cable fixing screws.
(4)Install the shorting bar to the LG and FG terminals of the GOT's power. Connect the ground cable of the connection cable with the GOT's ground cable to the FG terminal of the GOT's power. For GT1655 and GT155 , connect the ground cable of the connection cable to the FG terminal of the GOT's power, and connect the GOT's ground cable to the protective ground terminal. (Shorting is not needed.) When connecting the ground cables, each flat side of the two solderless terminals must be faced. For the details of wiring, refer to the User's Manual for the GOT used.
For the ground cable of the connection cable, use the following solderless terminals.
4.3 Installing CF Card Cover Fixing Screw The protective structure of the outside the enclosure for the control panel side installation unit is IP65 in shipping. For IP67 of the protective structure, follow the procedure below.
(1)Open the CF card cover, and remove the dustproof rubber in the direction of the arrow.
(2) Insert the CF card cover fixing screw into the hole of the CF card cover, and install the washer in the direction of the arrows.
4.1 Installing on GOT (1)Power off the GOT. (2)Remove one of extension unit cover of
the GOT and fit the GOT side installation unit in the GOT case.
(3)Fix the GOT side installation unit by tightening its fixing screws (2 places) with a tightening torque of 0.36 to 0.48Nm.
(1) Insert the control panel side installation unit into the installation hole of the control panel. For the installation hole, refer to the figure right.
Applicable solderless terminal RAV1.25-3, V1.25-B3A, FV1.25-B3A
0 (3.70 ) +0.08
+ 0 .0
GOT side installation unit
GOT A side
Control panel side installation unit
N LG FG L Ground cable
cable of GOT
N LG FG Terminal
(3)Close the CF card cover, and tighten the CF card cover fixing screw with a tightening torque of 0.11 to 0.48Nm.
4.4 Installation and Removal Precautions (1)When installing the CF card extension unit, make space of the
dimensions shown in the following figures inside the control panel. The bending radius of the cable must be the value shown in the following figures.
When installing the control panel side installation unit on the control panel, install the unit out of the way for the equipment inside the control panel, including the cables of extension units and the CF card interface of the GOT. Keep the distance of 25mm (0.98 inch) or more between the control panel side installation unit and the GOT. For the installation location, refer to the User's Manual for the GOT used.
(2)Extension units cannot be installed on the GOT side installation unit. When installing other extension units, install the GOT side installation unit at the last.
(3)When removing the GOT side installation unit, tilt PULL of the unit and remove the unit so as not to break the connector.
5. CF CARD INSTALLATION/REMOVAL PROCEDURE
5.1 Installation (1)Open the CF card cover and turn off the CF card access switch of
the unit. (2) Insert the CF card into the CF card connector with the front side
(3)Turn on the CF card access switch.
(2) When pressing the CF card eject button, the button pops out.
(1) Open the CF card cover. Turn off the CF card access switch and check that the CF card access LED turns off. (The CF card can be removed when the CF card access LED turns off even though the GOT's power is on.)
180 (7.09) or more
Unit: mm (inch)
100 (3.94) or more
18 to 23 (0.71 to 0.91)*
Control panel side installation unit
GOT side installation unit
*The dimension differs depending on the GOT
R(Bending radius of the cable) 55 (2.17) or moreR(Bending radius
of the cable) 55 (2.17) or more
WARRANTY Mitsubishi Electric will not be held liable for damage caused by factors found not to be the cause of Mitsubishi Electric; machine damage or lost profits caused by faults in the Mitsubishi Electric products; damage, secondary damage, accident compensation caused by special factors unpredictable by Mitsubishi Electric; damages to products other than Mitsubishi Electric products; and to other duties.
FOR SAFE USE This product has been manufactured as a general-purpose part for
general industries, and has not been designed or manufactured to be incorporated in a device or system used in purposes related to human life.
Before using the product for special purposes such as nuclear power, electric power, aerospace, medicine or passenger movement vehicles, consult with Mitsubishi Electric.
This product has been manufactured under strict quality control. However, when installing the product where major accidents or losses could occur if the product fails, install appropriate backup or failsafe functions in the system.
Country/Region Sales office/Tel Mitsubishi Electric Automation, Inc. 500 Corporate Woods Parkway, Vernon Hills, IL 60061, U.S.A. Tel: +1-847-478-2100 Mitsubishi Electric do Brasil Comercio e Servicos Ltda. Avenida Adelino Cardana, 293, 21 andar, Bethaville, Barueri SP, Brasil CEP 06401-147 Tel: +55-11-4689-3000 Mitsubishi Electric Automation, Inc. Mexico Branch Mariano Escobedo #69, Col. Zona Industrial, Tlalnepantla Edo. Mexico, C.P.54030 Tel: +52-55-3067-7511 Mitsubishi Electric Europe B.V. German Branch Mitsubishi-Electric-Platz 1, 40882 Ratingen, Germany Tel: +49-2102-486-0 Mitsubishi Electric Europe B.V. UK Branch Travellers Lane, Hatfield, Hertfordshire, AL10 8XB, U.K. Tel: +44-1707-28-8780 Mitsubishi Electric Europe B.V. Italian Branch Centro Direzionale Colleoni - Palazzo Sirio, Viale Colleoni 7, Agrate Brianza (MB), Italy Tel: +39-039-60531 Mitsubishi Electric Europe B.V. Spanish Branch Carretera de Rubi 76-80-Apdo.420, 08190 Sant Cugat del Valles (Barcelona), Spain Tel: +34-935-65-3131 Mitsubishi Electric Europe B.V. French Branch 25, Boulevard des Bouvets, 92741 Nanterre Cedex, France Tel: +33-1-55-68-55-68 Mitsubishi Electric Europe B.V. Czech Branch Avenir Business Park, Radlicka 751/113e, 158 00 Praha 5, Czech Republic Tel: +420-251-551-470 Mitsubishi Electric Turkey A.S. Umraniye Branch Serifali Mahallesi Nutuk Sokak No:5, TR-34775 Umraniye / Istanbul, Turkey Tel: +90-216-526-3990 Mitsubishi Electric Europe B.V. Polish Branch ul. Krakowska 50, 32-083 Balice, Poland Tel: +48-12-347-65-00 Mitsubishi Electric (Russia) LLC St. Petersburg Branch Piskarevsky pr. 2, bld 2, lit Sch, BC Benua, office 720; RU-195027 St. Petersburg, Russia Tel: +7-812-633-3497 Adroit Technologies 20 Waterford Office Park, 189 Witkoppen Road, Fourways, Johannesburg, South Africa Tel: +27-11-658-8100 Mitsubishi Electric Automation (China) Ltd. No.1386 Hongqiao Road, Mitsubishi Electric Automation Center, Shanghai, China Tel: +86-21-2322-3030 SETSUYO ENTERPRISE CO., LTD. 6F, No.105, Wugong 3rd Road, Wugu District, New Taipei City 24889, Taiwan Tel: +886-2-2299-2499 Mitsubishi Electric Automation Korea Co., Ltd. 7F-9F, Gangseo Hangang Xi-tower A, 401, Yangcheon-ro, Gangseo-Gu, Seoul 07528, Korea Tel: +82-2-3660-9530 Mitsubishi Electric Asia Pte. Ltd. 307 Alexandra Road, Mitsubishi Electric Building, Singapore 159943 Tel: +65-6473-2308 Mitsubishi Electric Factory Automation (Thailand) Co., Ltd. 12th Floor, SV.City Building, Office Tower 1, No. 896/19 and 20 Rama 3 Road, Kwaeng Bangpongpang, Khet Yannawa, Bangkok 10120, Thailand Tel: +66-2682-6522 to 31 PT. Mitsubishi Electric Indonesia Gedung Jaya 11th Floor, JL. MH. Thamrin No.12, Jakarta Pusat 10340, Indonesia Tel: +62-21-3192-6461 Mitsubishi Electric Vietnam Co., LTD. Ho Chi Minh Head Office Unit 01-04, 10th Floor, Vincom Center, 72 Le Thanh Ton Street, District 1, Ho Chi Minh City, Vietnam Tel: +84-8-3910-5945 Mitsubishi Electric India Pvt. Ltd. Pune Branch Emerald House, EL -3, J Block, M.I.D.C., Bhosari, Pune - 411026, Maharashtra, India Tel: +91-20-2710-2000 Mitsubishi Electric Australia Pty. Ltd. 348 Victoria Road, P.O. Box 11, Rydalmere, N.S.W. 2116, Australia Tel: +61-2-9684-7777
HEAD OFFICE : TOKYO BUILDING, 2-7-3 MARUNOUCHI, CHIYODA-KU, TOKYO 100-8310, JAPAN NAGOYA WORKS : 1-14, YADA-MINAMI 5-CHOME, HIGASHI-KU, NAGOYA, JAPAN
When exported fr
If you want to find out how the GOT1000 Mitsubishi works, you can view and download the Mitsubishi GOT1000 GT15-C08CF Card User's Manual on the Manualsnet website.
Yes, we have the User's Manual for Mitsubishi GOT1000 as well as other Mitsubishi manuals. All you need to do is to use our search bar and find the user manual that you are looking for.
The User's Manual should include all the details that are needed to use a Mitsubishi GOT1000. Full manuals and user guide PDFs can be downloaded from Manualsnet.com.
The best way to navigate the Mitsubishi GOT1000 GT15-C08CF Card User's Manual is by checking the Table of Contents at the top of the page where available. This allows you to navigate a manual by jumping to the section you are looking for.
This Mitsubishi GOT1000 GT15-C08CF Card User's Manual consists of sections like Table of Contents, to name a few. For easier navigation, use the Table of Contents in the upper left corner.
You can download Mitsubishi GOT1000 GT15-C08CF Card User's Manual free of charge simply by clicking the “download” button in the upper right corner of any manuals page. This feature allows you to download any manual in a couple of seconds and is generally in PDF format. You can also save a manual for later by adding it to your saved documents in the user profile.
To be able to print Mitsubishi GOT1000 GT15-C08CF Card User's Manual, simply download the document to your computer. Once downloaded, open the PDF file and print the Mitsubishi GOT1000 GT15-C08CF Card User's Manual as you would any other document. This can usually be achieved by clicking on “File” and then “Print” from the menu bar.