Summary of Content for Mitsubishi GOT2000 GT15-75QBUSL Bus Connection User's Manual PDF
GT15-75QBUSL GT15-75QBUS2L GT15-75ABUSL GT15-75ABUS2L
Thank you for choosing Mitsubishi Electric Graphic Operation Terminal (GOT).
2004 MITSUBISHI ELECTRIC CORPORATION
GOT2000/GOT1000 Series Bus Connection Unit
Prior to use, please read both this manual and detailed manual thoroughly to fully understand the product.
SAFETY PRECAUTIONS (Always read these precautions before using this equipment.)
Before using this product, please read this manual and the relevant manuals introduced in this manual carefully and pay full attention to safety to handle the product correctly. The precautions given in this manual are concerned with this prod- uct. In this manual, the safety precautions are ranked as "WARNING" and "CAUTION".
Note that the CAUTION level may lead to a serious accident according to the circumstances. Always follow the precautions of both levels because they are import- ant to personal safety. Please save this manual to make it accessible when required and always forward it to the end user.
Indicates that incorrect handling may cause hazardous conditions, resulting in death or severe injury.
Indicates that incorrect handling may cause hazardous conditions, resulting in medium or slight personal injury or physical damage.
Do not bunch the control wires or communication cables with the main circuit or power wires, or lay them close to each other. As a guide, separate the lines by a distance of at least 100mm (3.94 inches) otherwise malfunctions may occur due to noise.
[STARTUP AND MAINTENANCE PRECAUTIONS]
Before mounting or dismounting this unit to or from the GOT, always shut off GOT power externally in all phases. Not doing so can cause a unit failure or malfunction.
Use this unit in the environment that satisfies the general specifications described in the User's Manual for the GOT used. Not doing so can cause an electric shock, fire, malfunction or product damage or deterioration.
When installing this unit to the GOT, fit it to the connection interface of the GOT and tighten the mounting screws in the specified torque range. Undertightening can cause a drop, failure or malfunction. Overtightening can cause a drop, failure or malfunction due to screw or unit damage.
Before connecting the Bus connection cable to this unit, always shut off GOT power and PLC CPU power externally in all phases. Not doing so can cause a malfunction.
Insert and fit the bus connection cable into the connector of the unit to be connected until it "clicks". After fitting, check for lift which can cause a malfunction due to a connection fault.
Before starting cleaning, always shut off GOT power externally in all phases. Not doing so can cause a unit failure or malfunction.
Do not disassemble or modify any unit. This will cause failure, malfunction, injuries, or fire.
Do not touch the conductive areas and electronic parts of this unit directly. Doing so can cause a unit malfunction or failure.
Always secure the cables connected to the unit, e.g. run them in conduits or clamp them.Not doing so can cause unit or cable damage due to dangling, moved or accidentally pulled cables or can cause a malfunction due to a cable contact fault.
Do not hold the cable part when unplugging any cable connected to the unit. Doing so can cause unit or cable damage or a malfunction due to a cable contact fault.
Always make sure to touch the grounded metal to discharge the electricity charged in the body, etc., before touching the unit. Failure to do so may cause a failure or malfunctions of the unit.
Dispose of this product as industrial waste.
Make sure to transport the GOT main unit and/or relevant unit(s) in the manner they will not be exposed to the impact exceeding the impact resistance described in the general specifications of the User's Manual for the GOT used, as they are precision devices. Failure to do so may cause the unit to fail. Check if the unit operates correctly after transportation.
Manual The following shows manuals relevant to this product.
For relevant manuals, refer to the PDF manuals stored in the DVD- ROM for the drawing software used.
Compliance with the EMC and Low Voltage Directives To configure a system meeting the requirements of the EMC and Low Voltage Directives when incorporating the Mitsubishi GOT (EMC and Low Voltage Directives compliant) into other machinery or equipment, refer to "EMC AND LOW VOLTAGE DIRECTIVES" of the General Description included with the GOT used. The CE mark, indicating compliance with the EMC and Low Voltage Directives, is printed on the rating plate of the GOT.
Compliance with the new China RoHS directive (GT15-75QBUSL, GT15-75QBUS2L)
SJ/T11364 : GB/T26572
Referenced Standard: GB/T15969.2 (Requirement of Chinese standardized law)
Packing List The following items are included.
Manual name Manual number
GOT2000 Series Users Manual (Hardware) (Sold separately)
GOT2000 Series Connection Manual (Mitsubishi Products) For GT Works3 Version1 (Sold separately)
GT16 User's Manual (Hardware) (Sold separately)
GT15 User's Manual (Sold separately)
GOT1000 Series Connection Manual (Mitsubishi Products) for GT Works3
Note: This symbol mark is for China only.
Model Product Quantity
GT15-75QBUSL, GT15-75QBUS2L, GT15-75ABUSL, GT15-75ABUS2L
Bus connection unit 1
GOT2000/GOT1000 Series Bus Connection Unit User's Manual (This manual)
This user's manual describes the GOT2000/GOT1000 series bus connection unit (hereinafter referred to as the bus connection unit). Use the bus connection unit for making bus connection of the GOT. Refer to the User's Manual for the GOT used for the applicable GOT.
The performance specifications of the bus connection unit are indicated below. The general specifications of the bus connection unit are the same as those of the GOT. Refer to the User's Manual for the GOT used for the general specifications of the GOT.
* When the GOT power is on, the internal current consumption is included in the current consumption of the GOT. When the GOT power is off, the internal current is supplied from the power supply of the PLC system.
Select the used bus connection unit according to the connection target and connection position.
(1) Select the bus connection unit according to the connection target.
When using the bus connection, make the communication settings to perform communication between the GOT and PLC.
For the details of the bus connection, refer to the GOT2000 or GOT1000 Series Connection Manual (Mitsubishi Products).
Interface QCPU (Q Mode) bus connection
QnA/ACPU bus connection
Connector IN 1 1 1 1
OUT - 1 - 1
I/O occupied points
16 points (I/O assignment:16 intelligent points)
32 points (I/O assignment:
Special 32 points)
Internal current consumption
(5VDC)* 0.44A 0.44A 0.12A 0.12A
Weight 0.13kg (0.29lb)
(2) Select the bus connection unit according to the GOT connection position.
Placed midway : GT15-75QBUS2L/GT15-75ABUS2L
Placed at end : GT15-75QBUSL/GT15-75ABUSL GT15-75QBUS2L/GT15-75ABUS2L
QCPU (Q Mode), motion controller Q series : GT15-75QBUSL/GT15-75QBUS2L ACPU, QnACPU, motion controller A series : GT15-75ABUSL/GT15-75ABUS2L
3. PART NAMES AND EXTERNAL DIMENSIONS
Unit: mm (inch)
Dimensions of X when the bus connection unit is mounted to the GOT
Unit : mm(inch)
GT15- 75QBUSL 2.5(0.10)
GT15- 75QBUS2L 2.5(0.10)
GT15- 75ABUSL 4(0.16)
GT15- 75ABUS2L 4(0.16)
GOT GT27 GT25 GT16 GT15
15 10 (0.39) - 6.5 (0.26) 8 (0.31)
12.1 10 (0.39) 10 (0.39) 5(0.20) 5 (0.20)
10.4 10 (0.39) 10 (0.39) 8(0.31) 8(0.31)
8.4 10 (0.39) 10 (0.39) 10 (0.39) 10 (0.39)
5.7 10 (0.39) - 10 (0.39) 10 (0.39)
*1 2) 1) 17
Back view 3)
Unit : mm(inch)
*1 When the GT15-75QBUSL/GT15-75ABUSL is used, only the IN side connector is available.
4. INSTALLATION PROCEDURE
The installation procedure for the bus connection unit is explained using the GT1575.
(1) Power off the GOT.
(2) Remove two extension unit covers of the GOT.
(3) Fit the bus connection unit in the GOT case.
(4) Fasten the bus connection unit by tightening its mounting screws (4 places) with tightening torgue 0.36 to 0.48 Nm.
No. Name Description
1) Bus connector (IN side) Connector for connecting the bus connection cable (IN side)
2) Bus connector (OUT side)
Connector for connecting the bus connection cable (OUT side)
3) Extended connector Extension connector mounted to the GOT
4) Mounting screw Screw (M3 screw) for fixing the unit to the GOT
5) Rating plate -
(5) After tightening screws, attach the supplied stickers to avoid receiving electrostatic.
Warranty Mitsubishi Electric will not be held liable for damage caused by factors found not to be the cause of Mitsubishi Electric; machine damage or lost profits caused by faults in the Mitsubishi Electric products; damage, secondary damage, accident compensation caused by special factors unpredictable by Mitsubishi Electric; damages to products other than Mitsubishi Electric products; and to other duties.
For safe use This product has been manufactured as a general-purpose part for
general industries, and has not been designed or manufactured to be incorporated in a device or system used in purposes related to human life.
Before using the product for special purposes such as nuclear power, electric power, aerospace, medicine or passenger movement vehicles, consult with Mitsubishi Electric.
This product has been manufactured under strict quality control. However, when installing the product where major accidents or losses could occur if the product fails, install appropriate backup or failsafe functions in the system.
Country/Region Sales office/Tel Mitsubishi Electric Automation, Inc. 500 Corporate Woods Parkway, Vernon Hills, IL 60061, U.S.A. Tel: +1-847-478-2100 Mitsubishi Electric do Brasil Comercio e Servicos Ltda. Avenida Adelino Cardana, 293, 21 andar, Bethaville, Barueri SP, Brasil CEP 06401-147 Tel: +55-11-4689-3000 Mitsubishi Electric Automation, Inc. Mexico Branch Mariano Escobedo #69, Col. Zona Industrial, Tlalnepantla Edo. Mexico, C.P.54030 Tel: +52-55-3067-7511 Mitsubishi Electric Europe B.V. German Branch Mitsubishi-Electric-Platz 1, 40882 Ratingen, Germany Tel: +49-2102-486-0 Mitsubishi Electric Europe B.V. UK Branch Travellers Lane, Hatfield, Hertfordshire, AL10 8XB, U.K. Tel: +44-1707-28-8780 Mitsubishi Electric Europe B.V. Italian Branch Centro Direzionale Colleoni - Palazzo Sirio, Viale Colleoni 7, Agrate Brianza (MB), Italy Tel: +39-039-60531 Mitsubishi Electric Europe B.V. Spanish Branch Carretera de Rubi 76-80-Apdo.420, 08190 Sant Cugat del Valles (Barcelona), Spain Tel: +34-935-65-3131 Mitsubishi Electric Europe B.V. French Branch 25, Boulevard des Bouvets, 92741 Nanterre Cedex, France Tel: +33-1-55-68-55-68 Mitsubishi Electric Europe B.V. Czech Branch Avenir Business Park, Radlicka 751/113e, 158 00 Praha 5, Czech Republic Tel: +420-251-551-470 Mitsubishi Electric Turkey A.S. Umraniye Branch Serifali Mahallesi Nutuk Sokak No:5, TR-34775 Umraniye / Istanbul, Turkey Tel: +90-216-526-3990 Mitsubishi Electric Europe B.V. Polish Branch ul. Krakowska 50, 32-083 Balice, Poland Tel: +48-12-347-65-00 Mitsubishi Electric (Russia) LLC St. Petersburg Branch Piskarevsky pr. 2, bld 2, lit Sch, BC Benua, office 720; RU-195027 St. Petersburg, Russia Tel: +7-812-633-3497 Adroit Technologies 20 Waterford Office Park, 189 Witkoppen Road, Fourways, Johannesburg, South Africa Tel: +27-11-658-8100 Mitsubishi Electric Automation (China) Ltd. No.1386 Hongqiao Road, Mitsubishi Electric Automation Center, Shanghai, China Tel: +86-21-2322-3030 SETSUYO ENTERPRISE CO., LTD. 6F, No.105, Wugong 3rd Road, Wugu District, New Taipei City 24889, Taiwan Tel: +886-2-2299-2499 Mitsubishi Electric Automation Korea Co., Ltd. 7F-9F, Gangseo Hangang Xi-tower A, 401, Yangcheon-ro, Gangseo-Gu, Seoul 07528, Korea Tel: +82-2-3660-9530 Mitsubishi Electric Asia Pte. Ltd. 307 Alexandra Road, Mitsubishi Electric Building, Singapore 159943 Tel: +65-6473-2308 Mitsubishi Electric Factory Automation (Thailand) Co., Ltd. 12th Floor, SV.City Building, Office Tower 1, No. 896/19 and 20 Rama 3 Road, Kwaeng Bangpongpang, Khet Yannawa, Bangkok 10120, Thailand Tel: +66-2682-6522 to 31 PT. Mitsubishi Electric Indonesia Gedung Jaya 11th Floor, JL. MH. Thamrin No.12, Jakarta Pusat 10340, Indonesia Tel: +62-21-3192-6461 Mitsubishi Electric Vietnam Co., LTD. Ho Chi Minh Head Office Unit 01-04, 10th Floor, Vincom Center, 72 Le Thanh Ton Street, District 1, Ho Chi Minh City, Vietnam Tel: +84-8-3910-5945 Mitsubishi Electric India Pvt. Ltd. Pune Branch Emerald House, EL -3, J Block, M.I.D.C., Bhosari, Pune - 411026, Maharashtra, India Tel: +91-20-2710-2000 Mitsubishi Electric Australia Pty. Ltd. 348 Victoria Road, P.O. Box 11, Rydalmere, N.S.W. 2116, Australia Tel: +61-2-9684-7777
HEAD OFFICE : TOKYO BUILDING, 2-7-3 MARUNOUCHI, CHIYODA-KU, TOKYO 100-8310, JAPAN NAGOYA WORKS : 1-14, YADA-MINAMI 5-CHOME, HIGASHI-KU, NAGOYA, JAPAN
If you want to find out how the GT15-75QBUSL Mitsubishi works, you can view and download the Mitsubishi GOT2000 GT15-75QBUSL Bus Connection User's Manual on the Manualsnet website.
Yes, we have the User's Manual for Mitsubishi GT15-75QBUSL as well as other Mitsubishi manuals. All you need to do is to use our search bar and find the user manual that you are looking for.
The User's Manual should include all the details that are needed to use a Mitsubishi GT15-75QBUSL. Full manuals and user guide PDFs can be downloaded from Manualsnet.com.
The best way to navigate the Mitsubishi GOT2000 GT15-75QBUSL Bus Connection User's Manual is by checking the Table of Contents at the top of the page where available. This allows you to navigate a manual by jumping to the section you are looking for.
This Mitsubishi GOT2000 GT15-75QBUSL Bus Connection User's Manual consists of sections like Table of Contents, to name a few. For easier navigation, use the Table of Contents in the upper left corner.
You can download Mitsubishi GOT2000 GT15-75QBUSL Bus Connection User's Manual free of charge simply by clicking the “download” button in the upper right corner of any manuals page. This feature allows you to download any manual in a couple of seconds and is generally in PDF format. You can also save a manual for later by adding it to your saved documents in the user profile.
To be able to print Mitsubishi GOT2000 GT15-75QBUSL Bus Connection User's Manual, simply download the document to your computer. Once downloaded, open the PDF file and print the Mitsubishi GOT2000 GT15-75QBUSL Bus Connection User's Manual as you would any other document. This can usually be achieved by clicking on “File” and then “Print” from the menu bar.